Scan QR code or get instant email to install app
The motor name plate rating = 25 A
Refer NEC 430.32(A)(1) The overload protection of motor with service factor 1.15 and above shall have protective device with 125% of rated current.
Overload protection device rating = 25 x 1.25 = 31.25A
Refer NEC 240.6(A), the standard fuse ratings that can be used. In this case 30A fuse can be used to protect the motor